Name: Adam Roseberry
Hometown: Columbus, Ohio
Favorite Aspect of My Job: Crawl spaces, attics, and money
Hobbies: Golf, yard work, football
Role Model: Frank Moore
Interesting Fact About Me: I have 3 kids
Adam our tech was fantastic. Very knowledgeable and polite. Great job !
Adam had to correct issues from the installation of new furnace and a/c
Very good service. Polite and prompt
Wonderful. Very pleasant and knowledgeable
He was very nice and fixed my problem. Thank you.
Very friendly and knowledgeable technician. Very quick repair and all questions answered.
Very professional got along well with my husband
Arrived to find unit without pilot, ignited pilot and tested system all checks good. I explained operation to customer
Performed maintenance on complete system. All checks were excellent no issues found. Treated and cleared trap. Observed insufficient co detection in home recommended updating to more sufficient detectors (98$ per)
Arrived to find unit short cycling due to low pressure switch.
Polarity problems. Both units are working independently however not while twinned stemming from the dock repair from yesterday
Homeowner wanted bid to convert to a condensation pump, the entire system would have to re plumbed to accommodate, plenty of new existing 3/4 pvc we will need to bring assorted fittings as well as fittings to adapt to 2â€ pvc with a barbed fitting, est 3-500 $. I couldnâ€™t get to most of what I needed due to major renovation taking place my re evaluate
Performed maintenance on furnace. Removed and replaced aa213. All checks are good
Arrived to find stat off, i engaged call for heating and unit went through entire cycle and dropped out on low flame sensed. I removed and cleaned sensor and cleaned it. Restarted unit and couldnâ€™t get fault to occur again after sensor. Performed heating check all checks good filter was 3 months old
Arrived to find cam stat adjusted too high for fan on, adjusted to better spec to allow unit to cycle off as requested
Arrived to find unit working as requested, age of the unit is tremendous concern, unit running with very high heat rise and very inefficiently leaving several safety concerns as well as no co detection found or smoke detectors for that matter. Wasnâ€™t able to contact landlord
Arrived to find blower motor bad, est lv 10 1200-1500$ customer declined repair
Repair vent had existing leak
Removed and replaced high limit as well as igniter, experience two times board thought limit was open when it wasnâ€™t. After getting unit to run Iâ€™ve informed customer that board replacement is also a need due to inconsistent operation, customer declined repair at this time.
Arrived to find unit running very hot tripping out on high temp fan speed maxed out. Reduced gas pressure as much as I could still getting heat rise split 68-165 which is way too hot max was 75 degrees @ nearly 100 deg rise with no remaining adjustments outside of major cleaning and duct mods. Recommended new unit
Clogged condensation trap, high amp draw on inducer motor and also had a grinding noise. Recommended replacement unit for dependability moving forward to avoid potentially high repair cost
Arrived to find 2â€ double 45 (1 street 90) leak will need 12-16â€ of 2â€ pipe and previously stated 45s to
Arrived to find inducer motor full of water. Drain draining very slowly. Treated drain and blasted out trap.
Arrived to find bad igniter on trane :xe90 unit. Universal wasnâ€™t compatible.. upon replacement discovered primary limit wasnâ€™t making well and continued to kick off ingnition, ordering limit will return asap
Removed and replaced board. Wasnâ€™t getting voltage to inducer. Performed courtesy inspection all checks good
Customer had unit off upon arrival, I discovered that unit was tripping out on low flame sensed, cleanes sensor and restored heating operation, customer will call to schedule maintenance
Primary controls bad. Not getting volts to inducer. Customer consulting with husband needs bid
Main drain line is the problem large copper pipe w trap not draining
Returning to diagnose tomorrow afternoon- call Adam R with questions.
Arrived to find blower motor failed. Called Ferguson and ordered should be arriving tomorrow.. customer was approved to pay half of the repair cost upon repair and will make a payment for second half at later time. Customer declined ccm at this time
Arrived to find hum cartridge not seated into housing properly, cause leak when hum was running. Installed correctly and showed no signs of leak. Recommended new @@413 every 6 months
Arrived to find unit â€œoffâ€ I engaged unit to run in heating mode, it cam on per request and ran without issue. After talking with homeowner about alleged problem she stated she saw lights flashing in unit while unit wasnâ€™t running. I informed her that that indicates â€œnormal operationâ€ she also stated unit hasnâ€™t ever lost stat satisfaction call seems to be misunderstood operation. I did recall faults and unit did have 2 flashes siting to check pressure switch wires, I gave thorough evaluation of pressure switches, drain and vent and couldnâ€™t conclude any issues with unit. All checks are good, I did treat drainage with dawn