Name: Corey Beaudoin
Corey is a wonderful asset to your company he is knowledgeable and always willing to go the extra step to make sure our ac and heater are working as well as offering services which are beneficial to the longevity of our units. Thank you so much!
Technician was great, everything explained well. Happy with the service. Thanks Cory
Pleased with service
Corey did a great job servicing my HVAC system. I had several questions and he answered them right away, indicating his knowledge and experience.
Excellent job, very professional and friendly, good suggestions, will use again
very good job,very polite .Knows his job well,
The young man was very professional
demand service- failed ignitor
Install Quality Pledge
service and anniversary check.
ervice Call Platinum Client arrived to find system locked out due to tripped rollout. upon inspection found crack between two burners. this is a safety and potential fire hazard. condemned heat exchanger. estimate $5000-6000 to repair by replacing heat exchanger. recommend replacing unit due to age, condition, lack of maintenance by previous building owner. scheduled estimate for today at 1pm
Commercial Service Fee: repair motor bracket that was loose from other companys install of new motor blower has excessive vibration due to age and stripped out screws for blower housing mounting to blower deck. advised customer that there isn't really anyway to fix the vibration but could try a new wheel and housing assembly. customer Express concerns with sizing of furnace and AC and airflow in the building. does not cool the space very well. system is 14 years old, spoke to customer about replacing, wants estimate to replace and move system to loft above current furnace location
Service Call Platinum Client reprogrammed thermostat and set scheduling on one thermostat. other unit, diagnosed failed RTMA control board and burnt up transformer. system wired for 240v only receiving 210v wired for 208, transformer and board started smoking.
demand services d maintenance check
Service Call Platinum Client diagnosed control board failing, aftermarket board installed on lenox starting and restarting blower fan during call for heat. and do some motor pulling high ant s it's very hot to the touch and the seal on it is leaking recommend replacing a newer motor and control board estimate cost to repair around 1100 to 1400 dollars. system is over 10 years old and customer is second owner of equipment. system also shows signs of poor maintenance recommend replacing due to condition age and cost of repairs. customer would like to have estimate to replace will schedule for tomorrow.
service call no heat
The last home service provider you'll ever need!Request Appointment