Name: Corey Beaudoin
Technician was great, everything explained well. Happy with the service. Thanks Cory
Pleased with service
Corey did a great job servicing my HVAC system. I had several questions and he answered them right away, indicating his knowledge and experience.
Excellent job, very professional and friendly, good suggestions, will use again
very good job,very polite .Knows his job well,
The young man was very professional
service and maintenance check
Service Call After Hours Fee Diagnosed cause of water in-floor is due to a clogged drain trap preventing condensation from draining out of the drain pan. Cleaned drain with a shop vac, cleaned and flushed with water and dish liquid. recommended yearly maintenance checks and flushing drain periodically to prevent future clogging
Service Call Platinum Client diagnosed system freezing up due to dirty filter and being a little low on refrigerant. replaced filter added 2lbs R410arefrigerant. system operating normally at this time, verified 19-degree temperature drop. spoke to a customer about RGF reme halo and Halo led, customer, asked about humidifiers, quoted customer and provided information for Aa 700a and AA 800 STEAM HUMIDIFIER. The customer is going to talk it over with her husband
Work performed under GHAC Quality Pledge: Installed condenser fan motor, ran and tested equipment, spoke to a customer about surge protectors. installed surge protectors. system operating with 151/280psi. elevated suction pressure caused by heavy load(85 degrees inside the home)
Service Call Platinum Client: diagnosed condenser not starting due to failed capacitor, also found contactor to be pitted and buzzing due to poor contact. replaced capacitor and contactor cleaned coil. checked refrigerant pressures. The system is 30 years old, operates using R22 refrigerant. advised the customer of the age and condition of the system. the system is running and performing with an 18-degree temperature drop. the system will need to be replaced in the near future due to age. Signed customer up on Cozy Maintenance Plan.
Repaired refrigerant leak
Service Call Platinum Client the backside of the drain pan overflowing due to buildup in the sides of the drain pan cleaned the drain pan, put insulation tape across the back of the drain pan to prevent overflowing. cleared the drain, ensured proper draining, check refrigerant pressures to confirm the coil not freezing up. pressures are good, 115/270.
repair and maintenance
PERFORMED HVAC MAINTENANCE
The last home service provider you'll ever need!Request Appointment