Name: Trey Moellendick
Hometown: Vienna, WV
Favorite Aspect of My Job: Steady paychecks
Hobbies: golf, hiking, fishing
Role Model: My dad
Interesting Fact About Me: I have lost 120lbs
Furnace had one fault code #8 loss of flame. Could not reproduce fault code. Checked gas pressures. Incoming is 8.8” wc when off and 6.5 on high fire. Outlet pressures checked ok at 3.5 and 1.6. Checked resistance on pressure switches. Checked ok at 0 resistance individually and across the set. Found 1 very loose spade connector on a pressure switch. Inspected and tightened all of them. Gas valve appears to be over tightened causing wires to rub on the door. Ordering a new gas valve.
In Home Estimate
Estimate on Replacement
Thanks for a wonderful opportunity!
Quote for Dehumidification system and new drop duct and filter system.
Completed system maint. Check both heat and a/c replaced filter made minor drain repair covered by contract visit.
Renewal plat agreement
Customer is going to need new filter.. did not have available during time of service. Need to get price and availability for gas valve and throttle valve carrier mod. Furnace.
Checked and cleaned furnace and ac system is around 25 years old customer knows itâ€™s age and is interested in future replacement of furnace, a/c and possibly hot water tank
Bad igniter. Removed and replaced tested system operation all checks are good
The last home service provider you'll ever need!Request Appointment