Name: Trey Moellendick
Hometown: Vienna, WV
Favorite Aspect of My Job: Steady paychecks
Hobbies: golf, hiking, fishing
Role Model: My dad
Interesting Fact About Me: I have lost 120lbs
Best Advice to Customers: keep your filters clean
Good job. Very professional
He was very and knowledgeable. Answered our questions. Respectful, Polite.
Technicians are courteous and friendly.
Trey was very helpful. Answered all my questions and offered great advice on improving efficiency of my furnace.
He was great. Explained everything very well. Nice guy. Thank you!
Quote for Dehumidification system and new drop duct and filter system.
Completed system maint. Check both heat and a/c replaced filter made minor drain repair covered by contract visit.
Renewal plat agreement
Customer is going to need new filter.. did not have available during time of service. Need to get price and availability for gas valve and throttle valve carrier mod. Furnace.
Checked and cleaned furnace and ac system is around 25 years old customer knows itâ€™s age and is interested in future replacement of furnace, a/c and possibly hot water tank
Bad igniter. Removed and replaced tested system operation all checks are good
Observed Drain pan safety switch knocked out of position. Customer must have bumped switch causing it to engage safety shut off. Moved switch and tested system operation no further issues observed.
Arrived to find unit faulTing out on limit. Found filtrete carbon filter completely plugged up, recommended lessor filter and increased frequency changing every month no exceptions. Duct cleaning is recommended approximately 800$
Customer thermostat buttons failure. Replaced thermostat and checked system operation.
Replace blower motor and cap and thermostat.
Loose connection in breaker box. Possible breaker box issue want quote for smart breaker panel.
Replaced 16*25*1 filter. Replaced thermostat checked system operation
Cleaned flame sensor. Sold system for 6750...
System is in a state of complete failure 3 heat strips all burnt 2 sequencers burnt blower motor running half speed and blower wheel completely clogged.
Completed service agreement customer refused repair of 7.5 mfd run cap. If cap or motor fail it is not covered by any warranty
6404 aprilaire zone panel. Not working correctly since install of furnace.
Garage system furnace and a/c 20 yrs old in fair operating condition has normal signs of age and deterioration. System has reached its effective life span and will need replaced in the near future. Second system 1983 model 80% gas furnace with matching a/c extremely old and will be in need of replacement soon. System has failing ignition module and blower motor bearing making noise rusting heatexchanger etc. both a/c are in need of proper inspection, maintenance, and repair... should plan on replacing both systems within the first couple of years..
Replaced thermocouple and checked operation. Also repaired gas leak at union inside gas furnace.
Replaced pressure switch could not get system to malfunction but observed multiple pressure switch codes in fault memory.
System flashing stuck pressure switch verified problem and replaced sticking switch checked operation again.
Ignition module failed replaced and checked system is getting old and will need new system in the future.
Customer says system had limit fault did not observe any temperature problems checked system operation and system function.
Previous service charge to diagnose bad radiant floor control returned to replace and check operation.
Batteryâ€™s caused tstat to malfunction reset tstat and checked furnace system operation
Replaced 2 boiler thermostats.