Name: Ben Willard
Role Model: My brother
Interesting Fact About Me: Wrestled in College
Service Call Fee: ac not cooling. Found the unit low on refrigerant. The customer mentioned that it had been recharged and the motor had been replaced in the past. The customer is speaking with his wife about replacement options before making any decision moving forward.
Service Call Platinum Client: found system low on r22. Added 2lbs 12oz. Subcooling, superheat, and temperature drop are correct. the system is operating properly now.
Service Call Fee: AC not cooing well. only 10⁰F temp drop indoor upon arrival. found subcooling below factory specs. added 9oz of refrigerant. subcooling is perfect for factory specs now. 17⁰F temp drop indoor now.
Performed heating and cooling maintenance for customer
Furnace making loud noise in fan operation. The blower wheel is damaged. Ordered new warranty blower wheel.
HVAC SERVICE - INSTALLED REME HALO
Technician performed heating maintenance and supplied filter replacement.
Work performed under Quality Pledge
Service Technician performed diagnostic on furnace.
Replacement of Transformer
Installation of CO Detector
Install of pressure switch
HVAC SERVICE - replaced thermostat wire
HVAC Maintenance check of furnace and AC
Technician performed safety, health and efficiency inspection on heating and cooling systems.
Change out of humidifier pad to correct leaking from humidifier.
The last home service provider you'll ever need!Request Appointment