Name: John Kunkel
Thank you guys for being super affordable! I had called another company before you and they were charging $100 to just look at my unit. You tech was also very professional. Thank you for the plans you offer as well. We will be using you for all of our heating and cooling needs.
Got the job done quick and price was cheaper then I thought it would be would recommend
Serviceman was very knowledgeable. Very helpful!
On time. Identified problem. Ordered part. Again on time. Installed part. Tested system. Verified I was happy. All while making sure he made/left NO mess! Loved my experience and recommend them anytime.
He was wonderful. He found the problem and fixed it quickly
Install 2 reme halos
Added zone dampers and zone panel adapt old wires and added thermostat upstairs
Extend and terminate outside the fresh air vent with 2â€ pvc , pull power from the box to the AC unit , provide and install breaker for the AC unit. Leave behind vent for plenum ,pad tp fit the AC 30â€™ - 35â€™ Lineset , & disconnect box all included in this price.
Signed platinum agreement cleaned condesor coil and added one pound freon system cooling properly with 20 degree split
Complaint was No power was coming to the furnace. Upon arrival checking out the furnace found the neutral wire was arcing in the wire connector. Disconnected Power from furnace to breaker box henry Don Ohio voltage wire connectingâ€˜s. Installed a surge protector on both the furnace in the heat pump. Customer recently finished basement customers also complaint was downstairs stayed about 10Â° cooler in the basement suggestive closing off a couple runs in the upstairs to force more air in the basement. Another complaint, customer has older Honeywell thermostat 2 heat / 1 cool with a propane furnace and a heat pump outside. For the furnace to kick on propane he has to switch thermostat to emergency heat for propane. In the pass the thermostat would switch automatically. Going though programming thermostat was set to do so but would not change automatically. Recommend changing thermostat and covering over wires and cleaning them up more straightly. System has 2 zones. Zone one controls
Replaced induce motor and did Analysis on furnace. On age of furnace it is in rough shape but customer only wanted to repair due to money finances right now. System operating at this time. But will need to get ready for replacement
Replaced thermostat and added co monitor system operating properly at this time.
Did analysis on furnace and checked gas pressure. Also checked for leaks in gas line with leak searcher found no leaks and installed CO monitor
Thermostat was not giving 24 volts to AC was not sent. Replaced thermostat and 24 volts present signed platinum membership did platinum cleaning check system operating properly at this time.
Found ignitor had failed replace and upgraded thermostat in back side of home system operating properly and signed 2system Monthy platinum membership
Includes all miscellaneous materials and labor to completely install.
Replaced high pressure sensor on ac customer decline platinum service at this point.
Reversing valve had had ordering replacement as well as defrost board due to black charing on board
Call back on tech 3/12 found power off and gas shut off from tech called to check making sure we didnâ€™t lock out system but ended up being a mistake checked AC to make sure everything was working properly with that as well found capacitor readings failing. Replaced capacitor and AC operating properly at this time as well as the furnace
Customer had had a power surge tree falling on powerlines add caused the problem found in the furnace the transformer and the main control board has failed replaced both in furnace operating properly checking out the AC found the capacitor had failed due to it put surge protectors on both furnace and AC
Add two 8â€ inch supplies to both back rooms & A 8â€ supply to the room beside the living room. Also add 1 return & flex into the return drop.
Found switch failed repaired and system operating properly at this time.
Replaced piece gas line bring to code. Customer also has gas fire place found gas leaking but couldnâ€™t pin point location. Told customer we do not work on home fireplaces but shut off gas near hot water tank supplying gas to fire place and leak had stopped.
Evaluation of furnace found lack of return upstairs. Looking to add full system in attic and add steam humidifier to downstairs furnace
Replace blower motor and capacitor system operating properly at this time
Replaced surge protector on outdoor condesor unit that had failed. Operating properly at this time.
Replaced zone damper
Platinum membership heating and cooling service system operating properly at this time.
Drain lines clogged cleared system heating properly at this time.