Name: John Kunkel
It was great to get the Air Conditioning back working, especially during this heat wave. The Blower Motor definitely sounds different from the one we had before. Thank You Grogg's and John Kunkel taking care of us in less 12 hours from the time I called.
The two Tecs did good one was a trainee the other I have had him a few times good kid. He did my house in Bridgeport too
Would recommend Grogg's
Got to the house. Didn't mess around got right to the point.
From Erin in the office to our technician, everyone was wonderful.
Thank you guys for being super affordable! I had called another company before you and they were charging $100 to just look at my unit. You tech was also very professional. Thank you for the plans you offer as well. We will be using you for all of our heating and cooling needs.
Customer had leak in the line set, pumped down brazed in and vacuumed system. Work performed by John K.
Added refrigerant. Work performed by John K.
Service call for dual capacitor. Work performed by John K.
HVAC Service Agreement. Performed Platinum Comfort Club Membership Tune-Up on Heating & Cooling Systems. Work performed by John K.
Precision Tune-Up tune up on full system. Work performed by John K.
Braze leak in copper coil and added refrigerant. Work performed by John K.
Ran capacitor with other repair and direct drive blower motor. Work performed by John K.
Platinum Plus HVAC Monthly Agreement and capacitor. Work peformed by John K.
Service Call Fee: found older r 22 system low on charge customer wanted free estimate for replacement
WARRANTY REFRIGERATION COMPRESSOR Replace the compressor under warranty system operating properly at this time
HVAC Service Agreement
Performed Platinum Comfort Club Membership Tune-Up on Heating System
Performed Platinum Comfort Club Membership Tune-Up on Cooling System
Performed Platinum Comfort Club Membership Tune-Up on Cooling System Ac operating at temp, Amp draw at 80/% on compressor Would recommend looking at the options of equipment replacement. Equipment is 25 years old and functional. A/c could last the summer. Maybe,,,
Commercial Service Fee Furnace with A/c R-22 system froze up Notice oil leak on condenser coil and used leak detection device Do to ice accumulation unit has to sit till tomorrow to thaw Will need to top off r-22 and get sales man out for bid for ac replacement. Need to finish leak check on in door coil tomorrow.
Door on bottom of furnace was not on properly not allowing door switch to close
Cleared 3 drain lines that tide into main sewer system cooling properly
Service Call Fee: quoted customer to replace compressor and clean evaporator
Replaced gas valve system operating properly at this time.
Remove , replace wooden deck with new deck, and reconnect
Platinum heating and cooling. Found thermocoupler failed, replaced thermocoupler. Replaced filter, adjusted gas pressure was 3.9 now 3.5. System operating properly at this time
Performed platinum heating and cooling check. Replaced filter, checked gas pressure. Cleaned filter for humidifier and Outdoor coil. System operating properly at this time
Platinum monthly, tune up done (heating and cooling) found capacitor failed, replaced capacitor. System operating properly at this time
Replaced defrost board and fan relay board found modular failed that wasnâ€™t able to be seen until replacing two components