The professional team at Grogg’s Home Services has provided the residents of Flemington, WV with exceptional services since 1970! We are proud to offer great workmanship paired with affordable prices for all of your most important home comfort services. Make sure to call Grogg’s first for your air conditioner, heater, plumbing and window needs! Our services include repairs, installations and maintenance on heating, cooling, plumbing, windows and more that go above and beyond, every time.
You won’t find another company around with better reviews than ours! We invite you to read some of them below and find out why your neighbors consider us to be their nearby heating and air company and local plumber in Flemington, WV.
for Flemington, WV
Our Reviews by City
Heat pump cooling
Glass - Flemington, WV
Tech. checked out the system and located the defective electronic card causing the problem. The card needed to be ordered so cooling system was left so we could use until parts come. Satisfied with the service and on a holiday weekend to boot. Thanks!
Response from Grogg's Home Services:
Thank you for the great review and your confidence in our services. Please consider us for all your Home Services needs. Don't keep us a secret.
Service Call Platinum Client pumped refrigerant down into heat pump. uninstalled airhandler. capped off power wires. spoke to customer about duct cleaning, customer rwould like to add duct cleaning to furnace purchase. quoted customer pricing for duct cleaning.
A.O. Smith 50 Gallon Power Vent Water Tank
Service Call Platinum Client upon further diagnosis did clean flame rod and do believe unit to be overlimiting did disconnect byass on humidifier (it was piping supply air right back into return causing abnormal temp rise. did check drainage did nit find any issues. units temp rise was approximately 58 degrees co(0) was approximately 67 ppm did not get unit to have a malfunction problems could have been possibly flame rectification and or limit issues did address both issues. however unit is from 2003 and is in very poor condition do recommend replacing unit did set up quote for 1/5/22 also did check venting did not see any issues.
PERFORMED HVAC SERVICE FOR CUSTOMER
Connected new humidistat, turned on water, jumped 24v verified solenoid opening, set stat to 35, customer will let us know if issues occur.
Platinum maintenance check complete, ok at this time. Need to schedule to change steam humidifier canister. Do not have any in stock at this time. Replacements have been ordered.
Rewired power vent and furnace wiring, ok at this time.
Returning to diagnose tomorrow afternoon- call Adam R with questions.
Need to contact standard air to order drain for humidifier.
Found exhaust fan failed need to get replacement
Switch was off from check.
Customer was leaving need to reschedule
Performed platinum maintenance heating check, ok at this time.
Main floor tstat was not working, replaced, okat this time.