Grogg’s has served Flemington, WV with professionalism and expert heating and air conditioning since 1970.
See how we can help you with your heating and air conditioning requirements by reading our local Flemington, WV reviews.
for Flemington, WV
Our Reviews by City
Heat pump cooling
Glass - Flemington, WV
Tech. checked out the system and located the defective electronic card causing the problem. The card needed to be ordered so cooling system was left so we could use until parts come. Satisfied with the service and on a holiday weekend to boot. Thanks!
Response from Grogg's Heating & Air Conditioning, Inc. (Parkersburg):
Unit was off for code 15, dc bus undervoltage. Contacted tech support, incoming voltage was 252-254, was told that voltage is high, not allowing inverter to turn on compressor. After powering down and powering back on, was able to get unit to start. Allowed unit to run, checked pressure, and amps, ok at this time. Power company needs to be contacted per tech support due to incoming voltage to unit, and unitâ€™s allowable voltage.
Platinum service tune up found upstairs fuse tripped restored power and system operating properly at this time. Proformed platinum check.
System operating properly at this time. Customer had concerns when the unit comes on for the first 15 seconds the compressor makes noise. Tested compressor and unit working properly and amps. Are as they should be no problem found.
Replace outdoor control board, system operating properly at this time.
Found that outdoor board relay causing contactor to open and close intermittently. Need to order outdoor board. Temporarily bypassed board, will order.
Replaced drain pan, ok at this time.
Water had ran from coil section, down sides of furnace. Cut and cleared drain, seems ok at this time. If unit continues to leak, will need to replace drain pan.