Don’t let a surprise AC repair break the bank! Call the professional team at Grogg’s for exceptional home comfort services in Fleming, OH. We’ve served the area since 1970 with honest heating, air, plumber and electrician services that go above and beyond. Our experienced technicians provide repair, replacement and maintenance services on a number of systems for your home. We also offer discounts, financing and amazing warranties on services.
We invite you to read some of our reviews below from your neighbors in Fleming, OH. They will show our dedication and commitment to providing top notch customer service with every job we do.
for Fleming, OH
Our Reviews by City
Best service in the area!
Stuckert - Fleming, OH
The Puronics® Defender™ iGen® whole-house water softener is an excellent solution for budget-minded homeowners. The intelligent iGen® control valve adapts to your water usage lifestyle and adjusts regeneration to maintain consistent water quality and reduces operating costs. 10 YEARS PARTS & 1 YEAR LABOR.
Performed Platinum Comfort Club Membership Tune-Up on Heating System Cleaned and checked operation of air handler heat pump. Changed 16-25-1 filter. Verified working status of surge protection on air handler. No surge protector on heat pump, recommend installation of one.
Service Call Fee: Customer changed out tstat batteries and would not come back on to operate due to needing reset. Reset system and monitored system heat home from 64-70 in the home. Recommended having service done to check for any other issues. Customer wants to wait and see if this fixes the issue.
Service Call Platinum Client: arrived to find system off. Gave system a call. It ran without incident. I cleared drain on system it was dirty. Not exactly sure what the issue was but furnace is running ok for 25yrs old. Explained to customer that dependability is scarce at this age and I recommend they consider replacement
PROVIDED CUSTOMER WITH WINDOW REPLACEMENT ESTIMATE
Install Quality Control Check
Service Call Platinum Client removed and replaced 45/5 cap
Preformed heating and cooling check.
Add a 10â€ vent to the bottom of the drop to replace the 6â€ currently there
Performed annual maintenance on equipment.
Found ice collected around top of heat pump caused by gutter leaking and weather conditions. Removed ice inspected h/p operation and checked run cap. On both compressor and condenser fan motor. Replaced customer supplied filter.l