Looking for a true partner when it comes to your heating, air and plumbing needs in Mannington, WV? Connect with the team at Grogg’s Home Services! Proudly serving your area since 1970, you will love our affordable prices and friendly service. Our technicians are knowledgeable and experienced, so you can rest assured that your systems are in good hands. For repairs, installations and maintenance services you can trust, Grogg’s is your company!
Please check out our reviews below from clients near you in Mannington, WV. They demonstrate the commitment we have to providing exceptional customer service on every job we do each and every time.
for Mannington, WV
Our Reviews by City
Wilt - Mannington, WV 26582
Called for and issue with water overflowing and drained plug. They were very prompt on turnaround time for services. Our tech Corey was wonderful and professional!
Friendly staff and helpful by phone and on site. We appreciate you helping us!
Lepley - Mannington, WV 26582
Above and beyond!
Powers - Mannington, WV 26582
OK, This survey will be for both trips this week to keep our hvac up and running. If all your techs. are as courteous, efficient, knowledgeable, and just a nice as Kyle you have a winning team for sure. Keep up the great service. Thanks
Above and beyond!
Mike - Mannington, WV 26582
Very impressed with Kyle. He is extremely professional and friendly. Happy we went with Grogg's. Kyle arrived in 10 degree weather and stayed with the task until he found the trouble and had us up and running. Great Guy.
Installed ordered control board, verified operation
Performed Platinum Comfort Club Membership Tune-Up on Cooling System standing pressures on ac unit were 145 @ 46 ambient capacitor tested right at 45/4.7 capacitor within range cleaned compartment of bugs and webs did clean both condenser coils no issues however do strongly recommend adding surge protection to both outdoor unit or at the very least the minisplit condenser due to being very sensitive to electric surging or over current
Provided customer with HVAC estimate
HVAC Technician replaced capacitor.
Found switch failed repaired and system operating properly at this time.
Replaced heat exchanger in furnace, cycled furnace, ok at this time.
Furnace has compromised heat exchanger, flames rolling out. Need bid on replacement, current furnace seems to be oversized.
Warranty check complete, tested unit components, no issues found at this time. Filter changed.
Replaced start capacitor that had shorted out system operating properly at this time.
Cleaned drain system drain good at this time.