Looking for a true partner when it comes to your heating, air and plumbing needs in Glenville, WV? Connect with the team at Grogg’s Home Services! Proudly serving your area since 1970, you will love our affordable prices and friendly service. Our technicians are knowledgeable and experienced, so you can rest assured that your systems are in good hands. For repairs, installations and maintenance services you can trust, Grogg’s is your company!
Please check out our reviews below from clients near you in Glenville, WV. They demonstrate the commitment we have to providing exceptional customer service on every job we do each and every time.
for Glenville, WV
Our Reviews by City
Professional standards with hometown touch
Singleton - Glenville, WV
Response from Grogg's Heating & Air Conditioning, Inc. (Parkersburg):
Thank you for the great review and your confidence in our services. Please consider us for all your Home Services needs. Don't keep us a secret.
REPAIR WIRING Thermostat wire 3 feet. Work performed by John K.
Talked to customer about air conditioner being empty on R22. Talked about repair vs replacement, will call in with what they would like to do.
Arrived and found t-stat wires touching inducer housing and had melted through insulation. This caused low voltage short. Repaired wiring and replaced fuse. System fired off and is operating properly at this time.
Replaced thermostat and control board for heat pump under warranty.
Unit has a faulty thermostat and control board on heat pump. Unit will not shut off, wants to run even when there is no call for cooling. I believe that it has been running non stop for a long time now. Called lute about replacing board, they said that it is not under warranty. Recommended replacement of unit. Scheduled an estimate for new equipment Thursday 11-1.
Platinum service tune up system operating properly at this time.
Unit low on charge, due to age, customer wants to add refrigerant, and will look into having bid done depending on how long this lasts.
Window unit in wall, measures 19.5 by 25 1/2. Donâ€™t know if replacement can be done. Will send info to Keith.