Grogg’s Home Services is the company that Spencer, WV has remembered for excellent heating, air conditioning, plumbing and electrical services since 1970.
We never stop trying to give our valued Spencer, WV customers the best we have to offer for their HVAC, plumbing, electrical or home service needs. Read more in our reviews below!
for Spencer, WV
Our Reviews by City
Petitt - Spencer, WV
Fred was very knowledgeable and friendly. Fair prices and will call again.
Response from Grogg's Heating & Air Conditioning, Inc. (Parkersburg):
Thank you so much for your amazing feedback on Fred and confidence in our services. Be sure to keep in mind all of our services. Please don't keep us a secret
2 10ish yr old lg multi zone mini splits both low on refrigerant found leak in unit closest to the road could not locate leakage in the other unit. System closest to the road has leaking connections at flare fittings will require disassembly of system to repair leak test and recharge. Ballpark 700-1000$. Second system I sealed valves and time will tell if there are any other leaks in that system. Main section of home has no a/c and will not stay cool with current a/c system...
Move outdoor unit to roof, move electric to roof, 50â€™ line set, disconnect, pad
Flush kit, disconnect, 3 phase, low ambient kit
Arrived and found no low voltage. Immediately determined it was fuse popping from intermittent connection in older style glass busman fuse connector. Bypassed and put a standard blade fuse in. System is operating properly at this time.
Arrived and found both common and run wire burned at contactor. Replaced wires and system started. Pressures were a bit high from partially clogged coil. Cleaned coil and system is operating properly at this time.
Arrived and found compressor shorted to ground and took out a number of other electrical items. Would need to replace compressor, transformer, contactor plus auxiliary and coil sensor to get system functional. **Price Is liable to change due to price and availability of compressor. Due to age, condition, refrigerant type and cost of repairs it may be a more viable option to replace system
Installed new contactor with auxiliary and new transformer. New transformer is bad. Need to return with another transformer.
Arrived and found unit not receiving 24 volt signal due to failed contactor/transformer assembly. Ordering from Sid Harvey.
Chimney Service- Chimney Sweep
Unit was low on charge, added 2lbs 410a. Filter was so dirty it had sucked itâ€™s self into coil, theyâ€™re sending someone to replace
Chimney Service- Chimney Inspection