Looking for a true partner when it comes to your heating, air and plumbing needs in Nutter Fort, WV? Connect with the team at Grogg’s Home Services! Proudly serving your area since 1970, you will love our affordable prices and friendly service. Our technicians are knowledgeable and experienced, so you can rest assured that your systems are in good hands. For repairs, installations and maintenance services you can trust, Grogg’s is your company!
Please check out our reviews below from clients near you in Nutter Fort, WV. They demonstrate the commitment we have to providing exceptional customer service on every job we do each and every time.
for Nutter Fort, WV
Our Reviews by City
Always a pleasure
Watson - Nutter Fort, WV 26301
Always a pleasure to have Corey and Michael show up to service/repair or install maintenance for Furnace/Air Conditioner
Anderson - Nutter Fort, WV 26301
Blake - Nutter Fort, WV 26301
Cotern - Nutter Fort, WV 26301
The technician was very professional and arrived earlier then predicted. Fixed my furnace quickly and better yet, cheaply. Thanks Groggs
Great Service, even better technician!
Lafferty - Nutter Fort, WV 26301
Had an after business hours problem with furnace. Was contacted right away by the technician. John was courteous, knowledgeable and good at his job. He was very thorough with his inspection and had the furnace back up and running in no time. Thanks again!
Bohone - Nutter Fort, WV 26301
On time Serviced Furnace Replaced Filter Came back to finish the job Installed new Flexible ducting
He was very helpful and flexible
Bohone - Nutter Fort, WV 26301
He was very helpful in getting the furnace to run. I’m not sure if he changed the filter yet I’ll ask him tomorrow. He is to return tomorrow to finish the service.
Physicians - Nutter Fort, WV 26301
Response from Grogg's Home Services:
Thank you for the great review and your confidence in our services. Please consider us in the future for all your other Home Services needs. Don't keep us a secret.
Service Call After Hours Fee system not running due to no call for heat, wireless thermostat says it is set to heat. wireless control module indicating normal operation with no calls. inspected thermostat batteries and found that they are wet and corroded. batteries have failed preventing thermostat from sending signal. replaced batteries and cleaned out moisture. system operating normally at this time. advised customer that if this issue persists the thermostat may need to be replaced. advised customer that options would be the same thermostat, a Honeywell wireless or to run new wire for wired thermostat.
A.O. Smith 40 Gal Natural Gas Hot Water Tank
diagnosed condenser fan motor not starting on occasion. capacitor is a 3 microfarad testing at 3 microfarad. able to start motor by giving it a push start with a stick. advise customer that this means the motor is failing quoted motor and blade approximately $1,000 to repair. customer would like estimate to replace would like us to check availability on parts. scheduling estimate for replacement. also here to install automatic damper, supply house sent the wrong damper ordering correct damper.
Performed Platinum Comfort Club Membership Tune-Up on Cooling System 2018 comfortmaker furnace combo with a 1975 Lennox a/c using a 16x25x1 filter. Technician here in January addressed leak issue fixing pvc work, already extreme rusting through furnace however condensate pump is operational and no sign of active leaking at this time. Ensured clear drains, pump, collection box and inducer. Overall system is operating best it can, however a/c is on very borrowed time, coupled with prior leak issues most likely deteriorating life span of newer furnace. Customer would like a comfort advisor consultation about their options.
Performed Platinum Comfort Club Membership Tune-Up on Cooling System 2015 York split system w/ AA413 filter. Customer supplies own filters. Drains clear, cleaned condenser coil and flame sensor. Gas pressure at a good 3.2”wc and getting good low amp draws on major components. All checks good at this time. Would recommend surge protection to help better protect equipment. If interested we can provide a 120v for the furnace and a 240v for outdoor unit.
Performed Platinum Comfort Club Membership Tune-Up on Heating System did preform heating maintenance did clean flame sensor did read gas pressure lo 1.45 hi 3.22 temp rise lo 31 temp rise hi 51 ecm motor pulled approximately 3 amps inducer pulled 0.65 ran combustion analysis all numbers met safety and manufacturing parameters system operating properly. did sign customer up on cozy plus