Don't let a surprise AC repair break the bank! Call the professional team at Grogg's for exceptional home comfort services in Coolville, OH. We've served the area since 1970 with honest heating, air, plumber and electrician services that go above and beyond. Our experienced technicians provide repair, replacement and maintenance services on a number of systems for your home. We also offer discounts, financing and amazing warranties on services.
We invite you to read some of our reviews below from your neighbors in Coolville, OH. They will show our dedication and commitment to providing top notch customer service with every job we do.
The typical cost of air conditioning repair ranges between $200 and $1,000, with the average homeowner spending roughly $350 on AC repair. Most AC repairs are relatively inexpensive, costing less than $400, but some major repairs - like replacing a broken compressor - can cost over $1000. Ultimately, the price you’re quoted will depend on the parts and labor needed to fix the air conditioner.
Water heater repair costs, on average, about $585. Most water heater repairs cost between $218 and $953. Depending on the age of your water heater, it may be more cost-effective to just replace it. Your contractor will give you an honest opinion on whether to repair or replace at the time of your appointment.
If you have a circuit breaker that will not reset and quickly trips, the problem might be a short circuit. When a hot wire carrying current comes into contact with a neutral wire, a short circuit develops. A short circuit can damage appliances, cause overheating and even pose a fire threat. If you believe a short circuit is causing your circuit breaker to trip, turn it off and contact a certified electrician for repairs.
for Coolville, OH
Our Reviews by City
Sherry - Coolville, OH 45723
Grogg has sent very polite, knowledgeable technicians to our house. I like that they send a text when they are headed my way so I can put my dogs away.CoolvilleOH45723 39.2525-81.7875
Response from Grogg's Home Services:
Thanks for leaving us such a wonderful review. We are glad that you loved our services, our dedicated staff will be pleased to learn of your high praise.
Pamela - Coolville, OH 45723
Very goodCoolvilleOH45723 39.23-81.765
Vicki - Coolville, OH 45723
Service was provided with professionalism and efficiency coupled with kindness and friendliness. I felt comfortable with the work and the information provided.CoolvilleOH45723 39.2275-81.865
Enoch - Coolville, OH 45723
He did a very good job I would recommend himCoolvilleOH45723 39.245-81.78
Watson - Coolville, OH 45723
My geothermal stopped working and it was 81 degrees in the house. Got an appointment the next day. He was polite, efficient and knowledgeableCoolvilleOH45723 39.2525-81.7875
Great Service and would recommend
Enoch - Coolville, OH 45723
Great Service he was very politeCoolvilleOH45723 39.245-81.78
Response from Grogg's Home Services:
Thank you so much for this 5-star review. We really appreciate you being a customer and helping to share the word about us. We’re here for you anytime.
Polite, professional staff
Pletcher - Coolville, OH 45723
Winter - Coolville, OH 45723
Very pleased, Jessica did a great job, very ProfessionalCoolvilleOH45723 39.2175-81.805
Good job. Polite. Very informative. Pleasant personality.
Gentner - Coolville, OH 45723
Plesant personality, very knowledgeable in his trade. Got us up and running on a sweltering day. Good man.CoolvilleOH45723 39.185-81.77
Heat pump issue
DeHaven - Coolville, OH 45723
John was very professional, patience and knowledgeable. He diagnosed and fixed my heat pump and made recommendations for the future.CoolvilleOH45723 39.26-81.7575
Cooling maintenance on geothermal unit. Water temp in 66/out70. Refrigerant pressures of 118/227. Temp drop of 24 degrees. Cleaned drain with dish soap and cleaned coil with foam cleaner.
Maintenance check on heat pump system
Heil heat pump package unit using AA213 filter. Replaced filter. All checks good at this time. Customer is a monthly member and does not need to renew.
Performed cooling check on equipment. Changed 16-25-1 filter and installed surge protector and plasma air purifier. All checks were good with the equipment. Please send customer receipt.
Found capacitor on blower motor reading only a 1.5 on a 7.5 capacitor. Replaced part and found no other issues at this time. Filter size is 20-25-1 and still in good condition.
Installed 1” filter on top of furnace where previously there was none. Tested operation, confirmed. Sold 3 ton best duct cleaning for cleaning of the blower and ac coil.
Us timer said ac would not turn on. Was installed 7 months ago. Installer had mixed up some low voltage wires (see pictures). Re wired low voltage (see picture) confirmed working. Installed new stat.
AC maintenance visit. Performed full air conditioning maintenance checklist. Changed customer provided filter and verified working status of iWave. Found no issues with the system at this time.
Anniversary check on both systems. Changed air filters in both and canister for steam humidifier. Surge protection and Reme halos in good condition . Adjusted some settings in thermostat for second floor for when auxiliary kicks in.
Replace existing furnace and AC
Replaced faulty heat kit with new one.
Performed Platinum Comfort Club Membership Tune-Up on Heating System 2021 Heil split system w/16x25x1 filter. Heavy build up inside cabinet of furnace during last attempt for anniversary check. 70% eff flue piping had work done in September to fix previous issues, cleanliness possibly stemmed from that. Ensured clear drains, cleaned equipment, good gas pressures on heat and line temps for cooling, all electrical components in range with good amp draws. System is operating properly at this time.
Service Call Platinum Client- no faults present. Alarm history shows low refrigerant pressure code last night. Started system on a 58 degree morning and found system with a suction pressure of 115 and liquid of 193. Sub cooling of 4 degrees. System is cooling well(thermostat temperature of 70, supply temp of 47. Also changed air filter.
Performed Platinum Comfort Club Membership Tune-Up on Heating System: Performed year checks on the air handler. Replaced the filter. Checked amps on the blower motor and the heat strips. Evaporator coil is clean. Blower motor is clean. Checked temperature rise on the electric heat as well as the heat pump heat. All checks were good, found no issues at this time.
Performed Platinum Comfort Club Membership Tune-Up on Heating System Changed customer provided filters. All checks were good. Discussed comfort club renewal with customer and recommended surge protection. *Customer would like a call regarding service contract *
Service Call Fee: drain trap was plugged causing drain pan to over flow. cleared drain trap with pressurized nitrogen. also blew out the vinyl tubing for the condensate pump. added some cleaner to the reservoir tank of the pump to help clear out some of the build up in the line. coil is draining properly now.
Service Call back: Returned to a locked up condenser fan motor. It didn’t last through the season. Replaced the motor with a new one and double checked the temperatures. Everything checks out ok at the moment. System is still getting old. I still recommend replacement.