Looking for a true partner when it comes to your heating, air and plumbing needs in Wallace, WV? Connect with the team at Grogg’s Home Services! Proudly serving your area since 1970, you will love our affordable prices and friendly service. Our technicians are knowledgeable and experienced, so you can rest assured that your systems are in good hands. For repairs, installations and maintenance services you can trust, Grogg’s is your company!
Please check out our reviews below from clients near you in Wallace, WV. They demonstrate the commitment we have to providing exceptional customer service on every job we do each and every time.
for Wallace, WV
Our Reviews by City
Wickline - Wallace, WV
Performed Platinum Comfort Club Membership Tune-Up on Cooling System ran system in heating pressures and temp rise were perfect do not believe their their be any issue while cooling checked capacitor 45/5 tested at 44.3/5.1 pressures in heating were 130.8/339.9 temp rise 35
Service Call Platinum Client: furnace issue caused by dirty flame sensor. proceeded with maintenance check and signed up for cozy plus maintenance plan. cleaned flame sensor, changed filter, checked gas pressure, and performed combustion analysis. 96% efficiency with acceptable carbon monoxide production. furnace is lacking on return air, suggest modifying and going with 5" one year filter.
Commercial Service Fee: repair motor bracket that was loose from other companys install of new motor blower has excessive vibration due to age and stripped out screws for blower housing mounting to blower deck. advised customer that there isn't really anyway to fix the vibration but could try a new wheel and housing assembly. customer Express concerns with sizing of furnace and AC and airflow in the building. does not cool the space very well. system is 14 years old, spoke to customer about replacing, wants estimate to replace and move system to loft above current furnace location
Service Call Platinum Client upon further diagnosis did discover defrost board to be failed as well at sensor did manually close sensor and unit would kick defrost for approximately 15 seconds. did quote for repairs customer would like a bid due to condition of system, system is 8 years of age but was not registered. did call standard air to confirm. did sign customer up on maintenance.
PROVIDED CUSTOMER WITH HVAC ESTIMATE
Added zone dampers and zone panel adapt old wires and added thermostat upstairs