For exceptional heating, AC, electrician and plumbing services in West Union, WV, turn to the pros at Grogg’s! In business since 1970, our family owned and operated business provides repair, replacement and maintenance service on your home’s most important systems. We also offer indoor air quality, water filtration and window replacement services. Our team is ready to help with your entire home!
Curious why we have so many incredible reviews? We have a lot to offer our clients, from amazing warranties to precise workmanship performed. In addition, we are available to you 24/7 for emergencies. Please read our reviews below and find out why your neighbors consider us to be the only heating and air company and local plumber they call in West Union, WV.
for West Union, WV
Our Reviews by City
Chad - West Union, WV 26456
Matt was great. Very friendly and thorough.
Response from Grogg's Home Services:
Thanks for leaving us such a wonderful review. We are glad that you loved our services, our dedicated staff will be pleased to learn of your high praise.
Excellent Customer Service
Kim W. - West Union, WV 26456
I’m so glad I chose Grogg’s for our garbage disposal problem. Jordan H. was knowledgeable, professional, efficient, and easy to work with. I will definitely consider Grogg’s in the future.
Fast and dependable
Turner - West Union, WV 26456
Very polite, honest, and courteous service person.
Ben was awesome, definitely recommend Groggs for all your ac repair. Awesome people
Nicole2008 - West Union, WV 26456
Rye - West Union, WV 26456
Performed anniversary check on furnace and air conditioner. Changed customer provided AA413 filter. Recommend surge protection and discussed comfort club renewal with customer. Renewed for another year.
Customer said condensate pump was leaking. Tested pump. Pump worked, however had a crack in the tank from top to bottom. Replaced pump. Tested new pump twice. Confirmed operation. Also fixed a kink in the tubing.
2022 Ruud package unit using AA313 filter. All checks good at this time and system is operating properly. Customer had previous issue during cold spoke with outdoor regulator on gas line freezing. Heating check has since been already done and gas pressures checked/adjusted but just noting in case future issue.
Package unit installed 2007 is putting out high levels of carbon monoxide (700ppm). Limit switch on it has been bypassed causing damaged to the heat exchanger. Customer has had multiple issues this unit and is ready to replace it. Customer is getting an estimate today 1-3pm to replace package unit.
Cleaned all duct and washed all grills. Informed customer that old White return grill are faded and look dirty but are clean. Installed 2 reme halos and confirmed operation. Informed customer that it smells persist out of certain vents flex duct may need replaced. Informed customer some boots are falling out due to subfloor damage.
Customer said furnace was not working and heard a loud pop at the stat. Looked over the furnace and diagnosed a bad stat. The pop was one of the batteries blowing. Replaced stat, tested and verified operation. Also informed customer of rust in the heat exchanger.
Warranty inducer and pressure switch
Thermostat showed outdoor equipment fault once when customer switched to cooling yesterday but the unit has been working for them. Checked outdoor unit. Refrigerant charge was off from when we charged it when it was cold outside. Added 10 oz of refrigerant to correct refrigerant charge. Left system running with a 114/218 refrigerant pressure and 20 degree temperature drop.
Outdoor unit was out of refrigerant. Nitrogen test found leak on low pressure sensor line. Repaired leak and leak tested with nitrogen. Pulled vacuum and refilled system with 12 lbs of refrigerant.
Cleaned and checked one year old equipment. Changed customer provided filter and installed surge protection. Customer would like a reminder next month about maintenance plan.
Blower wheel needs cleaned, and upgrading the filter to a 1yr* filter to eliminate the washable filter.
11 yr old Goodman air handler had a mouse in the blower wheel causing bad vibration. Pulled blower to remove mouse and put back together. Customer was using supplemental propane heat and expressed having headaches using it. I checked for carbon monoxide but didn’t find any readings of it. Recommended carbon monoxide detector in the home. They have elected to get one themselves rather than use provide one for them. Customer was also concerned about a burning smell. Smell was coming from dust burning off the electric strips and smell will dissipate.
Furnace flame sensor was dirty. Annual maintenance check was due in the next couple months, so we just did the tune up today.
Install 4 head minisplit system
22 yr old Goodman furnace. Draft motor is receiving constant voltage keeping the pressure switch from reopening to restart the lighting process. Draft motor was very hot from constant running. Also the furnace cuts out after about 10 minutes on high temperature limit. Wires on draft motor are damaged from being pinched against door and motor. Estimate repair of control board is $500-700. Draft motor has a high chance of failing soon from constants running. Estimate draft motor repair is $600-900. Customer has declined getting a quote for replacement and plans on fixing furnace themselves.
No issues found with 2017 York furnace. Unit operates with out fault every time we tried. Checked drain, gas pressure, combustion analysis, and flame sensor. Showed customer how to read code if issue comes back. I checked the outside vent as well and informed them to make sure vent was clear and didn’t have ice formed on it if they have an issue.
Service Call Platinum Client- 2011 Goodman package unit. System was unable to light due to low gas pressure. Increased pressure from 2.4 up to 3.2 inwg. Also cleared out any cob webs that may have been in the gas orifaces. System is up and running now and passes combustion analysis for safe use. System is using well gas that is rough on a system. Customer may want to think on replacing the unit in the near future.
Service No Charge Found 24 v fuse to be blown . Turned u it on into cooling and inspected contactor for a short put unit into cooling to verify, unit did not blow fuse checked for rubouts on furnace did not find any. Replaced fuse and unit ran meeting all parameters. Took amp draw on transformer and only pulling 1.08 amps. Could have been a weak fuse. Furnace isn’t in very good condition their is a lot of moisture in basement.